About the Project:
This job was a small terrace home in paddington that was experiencing sewage overflow from the boundary trap access lid located on the front step.
When we attended to the house to inspect the cause of the blockage we shined a torch down the lid of the boundary trap to see that it was not holding a water seal due to the large cracks allowing the water to drain into the soil. This will cause the sewerage waste to not flow away in its correct manner and create a surcharge.
How We Fixed It:
With a commercial wet vac we removed all the water from the boundary trap and cleaned the pipe in preparation for relining. WIth the use of our Brawoliner relining method we relined the pipe from the lid of the boundary trap down to the junction on the Sydney Water Mains connection. On completion we robotically resinated the junction to the house line so the drains could flow in their correct manner.